The WM-PC Series economy plastic water meter is excellent for residential water metering. It uses the multi-jet principle to measure flow totals. The gear train drives the register totalizer dials. In addition, a pulse
output is an option when you want to send the data to a remote location. The 1/2", 3/4" and 1" meters come set with 1 Pulse/Gallon (3/4" Cubic Feet set for 1 pulse/cubic ft) and the 1 1/2" meters come set with 1 Pulse/10 Gallons. This water meter is BPA free and NOW ARE NSF 61 CERTIFIED to meet lead free regulations. They are also designed to meet the AWWA C708 Standards.
These meters are frequently used as a low cost solution for residential water measuring. This product is the rare example of when inexpensive doesn't equal "cheap"! It's one of the least expensive water meters on the market and ideal applications would be using the WM-PC as a Sewer Deduct Meter or Summer Meter to monitor water that is used outdoors and never passes through to the sewer system. Many municipalities will allow home owners to deduct their outdoor water use from their sewer bill.
All meters come with plastic fittings.
*NOTE - Bulk discounts for basic meter only. Not applicable to add-on items like garden hose adapters
|Model No.||Size||Flow Rate (GPM)||Normal Flow (GPM)|
|WM-PC-050||5/8" X 1/2"||20||10||0.25||1-20|
|WM-PC-075||5/8" X 3/4"||20||10||0.25||1-20|
|WM-PC Materials & Specifications|
|Temperature||105⁰ F (40⁰ C) max|
|Pressure||150 PSI operating max|
|Materials Body/Couplings||FRP (fiber reinforced polymer)|
|Accuracy||+/- 1.5% within normal flow rate|
|Maximum Current||20 mA|
|Maximum Voltage||24 Vdc or Vac|
|Cable Length||4.5' (1.35m) std (2000' max run)|
Once the adapter ends are installed on the upstream and downstream pipes, the meter is installed by tightening the collar nuts onto the inlet and outlet of the meter. These "true-union" fittings then allow the meter to be easily rotated to the proper orientation (face up), or removed for cleaning, repair, or replacement.
These meter threads look practically identical to the NPT adapter threads BUT THEY ARE NOT!
Trying to install the meter without the adapter will damage the pipe's threads, the meter's threads, or BOTH!
23 Reviews Hide Reviews Show Reviews
Was a great product for what I needed, along with a reasonable price. Lets me watch my well.
I'm getting accurate pulse readings on this meter so far. 1 pulse = 1 gallon. I'm using it in my backyard tomato garden. I need a low flow system to keep water bill down, and the 1/2in. meter (with NPT adapters) is adequate for my flow. Water meter has standard counters but I only need pulses to show up on cloud server. This does the job.
I've purchased a few of these to hook up with ice machines for filter changing. I also got a cheap digital counter to hook the meter to for number of gallons. Everything has been working good so far.
Meter is well built & seems to function correctly. Either the instructions on how to read it are labeled incorrectly or the metering display & dials are from the 1/2"-3/4" meter. Was shipped promptly & delivered on time. Great service.
RESPONSE FROM FLOWS.COM:
Thanks for the feedback! Yes, the manual you have is incorrect. The meter face changed for the 1" when we got it NSF certified. The 1" now reads like the 1/2" and 3/4" meters. The manual is changed on the site. Here's the link: http://www.flows.com/content/literature/Manuals/AA_User_Manual_WM-PC.pdf
We'll make sure the correct manuals are shipped in the future. Thanks again!
These are excellent units for the price. They come with adaptors to reduce the 1" fittings to 3/4". Dial is easy to read
What a quality piece of equipment I just installed into my home well water system. Having a MANUAL water softener, I've been guessing as to when to recharge (36,000 grain). Now, by knowing the water's hardness (17 gr/gal) and how many gallons are being use (NEW METER) I will know exactly when to recharge with out being too early or late.
I have been using it to control de water consumption at home, using the pulse sensor. I t has been installed for almost a year now without any problem. I hope it continues like this for some more years.
Worked just as promised. Seemed accurate at variable rates. Very cost effective product.
We have installed these for 60 apartments
and they do a good job of passing the water costs on to the tenants. They have also helped to identify some water leaks we were not aware of.