This 5/8" X 3/4" Direct Read Lead Free Brass Water meter by Neptune is the perfect meter for residential water metering applications. It's certified lead free and can be ordered to measure in Gallons or Cubic Feet. In addition, this meter is pit rated (can be installed in an underground pit). Couplings are included with this meter. This is a direct read meter only. No remote reading capabilities available with this model.
- MADE IN THE USA
- Max Flow Rate: 3/4" - 20 GPM 1"- 50GPM
- Max Operating pressure: 150 PSI
- Max Temp: 120°F (Direct Read Only)
- +/- 1.5% Accuracy within normal flow (95% accurate in Low Flow)
- Nutating Disc
- Sealed Register with Magnetic Drive
- Low Flow Indicator
- Approved for Horizontal or Vertical Flow Positions
- Couplings INCLUDED
- Direct Read Meter Only. No remote reading available with this model.
- Other Neptune meters available. Call for details
For typical applications, this meter requires 10x's the pipe diameter upstream and 5x's pipe diameter downstream.
SEE PRODUCT VIDEO TAB TO SEE HOW TO ROTATE THE REGISTER
10 Reviews Hide Reviews Show Reviews
Excellent Quality....Great Price
I worked in the water industry for over 20 years. I changed industries to the distillation of air. When asked to find an inline low cost flow meter only a few names came to mind. I researched the flow meters that were on my short list and the Neptune was the best, hands down. Not only in the specs that were available but I have worked with Neptune meters as I stated for over 20 years and their reliability is outstanding.
super fast delivery
Quick delivery and Great Price
This unit was easy to install, robust and complete with brass union fittings. So far it's giving me an accurate read.
Product Just as Described. I was looking for an exact replacement water meter, and this meter was what we needed. Fit in the exact spot the old meter was removed from.
This is a great water meter. I have installed it before and will continue to use this model since it is reliable and easy to install.
Easy to connect. Works like a dream. Connected to house main line.
Leak detector awesome!
quality looking and feeling product. I installed it inline on one of my cpvc pipes coming from my water well at my home.
Easy to install and has been working ok for about a week now. also installed a pressure guage at the same time. I previously could not monitor the well since all equipment for the well is outside the house in a casement.
I am really pleased with the whole thing including the leak detector spinner that already helped detect a water leak in a line to my horse stable.